Water softener ForHome® Cab120 35 lt. Cabinet Resin with Automatic Volume-Time Valve
The volumetric valve can be programmed with four types of regeneration: mixed time / volume regeneration, time chronometric, immediate volumetric, delayed volumetric. Timed timekeeping - after the number of days programmed, immediate volumetric - at the passage of a certain quantity of water, delayed volumetric - from the volume of water and the programmed time, mixed volumetric time / volume - similar to delayed regeneration, but allows to program a safety regeneration after the number of days programmed. The steps necessary to ensure that the system works properly are only to check that it is connected to the electricity grid and that there is a sufficient amount of salt. The only requirements for installation are the connection to electricity and three pipes (inlet, outlet, drain). Bypass and mixing valve to adjust the hardness at the outlet included in the system. CE, NSF, D.M. certified product 25, D.M. 174.
Example of calculation to determine the correct article
A 25 liter resin softener with a hardness of 40 ° F (medium high hardness), develops 3,500 liters of softened water (140: 40 = 3,500). In this case, 3,500 m3 must be programmed in the softener's treatment capacity using the keys on the display and the softener will supply limestone-free water at zero French degrees.
Output hardness adjustment
It is advisable not to dispense completely softened water in domestic installations. The CS range softeners have an integrated residual hardness regulator that allows you to precisely adjust the hardness of the treated water. To adjust the residual hardness, the MIX valve regulator must be opened gently. All water softeners are supplied with this valve completely closed and therefore will supply water at 0 ° F. For water intended for human consumption we recommend a residual hardness between 5 and 10ºF for copper pipes and between 8 and 10ºF for iron pipes. Depending on the programmed output hardness, the softener will tend to produce more softened water and less salt consumption because the input hardness must be compensated with the output value. A 25 liter resin softener with an inlet hardness of 40 ° F and an outlet hardness of 5 ° F, develops 4,000 liters of softened water (140: 35 = 4,000). In this case, 4.0m3 must be programmed in the softener treatment capacity using the keys on the display. On average a person consumes 150 liters of water a day and a timed programmed regeneration is recommended every 4/5 days, therefore a family of 4 with water at 40 ° F consumes for 5 days. 3,000 liters, therefore a 25-liter softener with programmed regeneration can also be set at 6 days.
Benefits and advantages
Reduction of the hardness of the water, which is the cause of scale. ENERGY SAVING: the device prevents the formation of incrustations in the pipes and ducts. Greater sense of well-being during the shower. Soft and clean skin. Increased life span of household appliances and boilers. ECONOMIC SAVINGS: reduction in the use of soaps, fabric softeners and chemicals. Reduced maintenance costs. Fully automatic operation. All you need to worry about is adding salt to the softener.
* Minimum pressure: 1.4 bar (1.4 kg / cm2)
* Max pressure: 8.6 bar (8.6 kg / cm2)
* Min temperature: 4 ° C
* Max temperature: 43 ° C
Specifications of the CAB120-35 35 lt model. resin (suitable for 8/9/10 people)
* Exchange capacity: 196ºHFxm3
* Salt consumption for regeneration: 5.8 kg / salt.
* Water consumption for regeneration: 306 lt.
* Quantity of treated water for regeneration, 35 ° F-5,600m3, 40 ° F-4,900m3, 45 ° F-4,355m3, 50 ° F-3,920m3, 60 ° F-3,266m3.
* Working flow rate: 1.0 m3 / h
* Max flow rate: 1.5 m3 / h
* Water inlet / outlet: 1 "
* Dimensions mm (LxPxH): 334x570x1350
We recommend the use of the chlorine manufacturer for the automatic sanitization of the resins at each regeneration. In Italy it is recommended by law for other countries such as France, Germany, Austria, it is not foreseen. (See code - 15000407).
Furthermore, to safeguard the system and the entire system from pebbles and various sediments in suspension, the installation of a housing with cartridge inside in wire-wrapped polypropylene with a filtering density of 50 microns or higher is recommended. (see code - 02001014 Vessel container + code 04001002-05 50 micron filter)
- Cabin softener
- By-pass valve
- Instruction booklet
RECOMMENDED ACCESSORIES (SEE ACCESSORIES):
- code 02001014: VESSEL KIT FOR SEDIMENT FILTER
- code 04001002-05: 50 MICRON SEDIMENT FILTER
- code 13000001 - TITRANT FOR HARDNESS SETTING
* Softeners are supplied without salt, uti is recommended